Each DSCA40/41 voltage input module provides a single channel of analog input which is filtered, isolated, amplified, and converted to a high-level voltage output. Signal filtering is accomplished with a five-pole filter. An anti-aliasing pole is located on the field side of the isolation barrier, and the other four poles are on the system side. After the initial field-side filtering, the input signal is chopped by a proprietary chopper circuit. Isolation is provided by transformer coupling, again using a proprietary technique to suppress transmission of common mode spikes or surges.
Module output is either voltage or current. For current output models a dedicated loop supply is provided at terminal 3 (+OUT) with loop return located at terminal 4 (-OUT). The system-side load may be either floating or grounded.
Special input circuits provide protection against accidental connection of powerline voltages up to 240VAC and against transient events as defined by ANSI/ IEEE C37.90.1. Protection circuits are also present on the signal output and power input terminals to guard against transient events and power reversal. Signal and power lines are secured to the module using screw terminals which are in pluggable terminal blocks for ease of system assembly and reconfiguration.
The modules have excellent stability over time and do not require recalibration, however, zero and span settings are adjustable up to ±5% to accommodate situations where fine-tuning is desired. The adjustments are made using potentiometers located under the front panel label and are non-interactive for ease of use.
Frequently Asked Questions
Can Dataforth provide calibration reports for modules I purchased?
Yes we can provide calibration reports for the modules that you purchased.
You can either
a) visit https://www.dataforth.com/TestDataReport.aspx to search for Test Report Datasheets by Serial Number or
b) you can send us a list of model numbers and their serial numbers to email@example.com
Could you explain, what is the main difference between the DSCA41 and the DSCA49?
The main difference is the DSCA41 is an input module and the DSCA49 is an output module, which means:
A. The DSCA41 module has its input on the isolated field side of the module, connected to it through screw terminals 6 and 7. The DSCA41 module has its output on the system and power supply side of the module, connected to it through screw terminals 3 and 4.
B. The DSCA49 module has its output on the isolated field side of the module, connected to it through screw terminals 6 and 7. The DSCA49 module has its input on the system and power supply side of the module, connected to it through terminals 3 and 4.
Keywords/Phrases: DSCA, DSCA module, DSCA input module, DSCA output module, DSCA41, DSCA49
Does Dataforth have any DSCA modules that can operate on a 12Vdc power supply?
Dataforth does not have any custom modules that run on 12VDC power. Most DSCA modules require a minimum power supply voltage of 15VDC while some require a minimum of 19VDC. Both are suitable for use with nominal 24VDC power supplies over the full operating temperature range of -40C to +85C. Dataforth offers a line of accessory power supplies, PWR-PS5RxW, which have been qualified for use with the DSCA product line. https://www.dataforth.com/catalog/pdf/PWR-PS5RxW.pdf
How do I convert an RMS voltage to its corresponding peak voltage?
To convert an RMS voltage to its corresponding peak voltage, you simply take the RMS voltage value and multiply it by the square root of 2, or roughly 1.414.
For example, 1500Vrms corresponds to a peak voltage of 1500 * 1.414 = 2121 Vp
If the input range of my signal conditioner is -1V to +1V and the output range is 0 to 10V, does this mean that it ignores polarity?
A signal conditioner with these I/O ranges does not mean that the module ignores the polarity of your voltage input. The output of voltage input modules are scaled linearly, meaning an input of -1V would correspond to an output of 0V, an input of 0V would correspond to an output of 5V, an input of +1V would correspond to an output of 10V, and so on.
How does the load resistance of a module affect the noise at the output?
Noise at the output of a module is independent of load resistance.
What is the output resolution of the DSCA series?
The DSCA series is completely analog, so the output resolution cannot be expressed in terms of bits as it is not a digital signal. The only thing that would cause any uncertainty/lack of clarity in your output signal would be the output ripple and noise, which is rated at a typical value of 0.025% span RMS as listed in the datasheet.
View Dataforth cross-reference data.
- No cross reference is available.
The information available through this competitive cross reference guide are based upon product catalog information obtained from a variety of sources. The competitive cross reference information is being provided to you free of charge for your use. While Dataforth Corp has used reasonable efforts to ensure data accuracy, Dataforth Corp does not guarantee that it is error-free, nor does Dataforth Corp make any other representation, warranty or guarantee that the information is accurate, correct, reliable or up-to-date. Dataforth Corp expressly disclaims all implied warranties regarding this information, including but not limited to any implied warranties of merchantability or fitness for a particular purpose.
This information is provided only as a convenience on an "as is" basis and Dataforth Corp. or its representatives or distributors are not responsible for any incorrect, inaccurate, or incomplete information. You are solely responsible for (1) selecting the appropriate Dataforth products for your application, (2) designing, validating and testing your application, and (3) ensuring your application meets applicable standards, and any other safety, security, or other requirements.