The MAQ20-DIOL discrete input/output module has 5 isolated discrete input channels and 5 isolated discrete output channels. Input channels accept 3-60VDC signals and output channels switch 3-60VDC signals at up to 3A load.
The MAQ20-DIOH discrete input/output module has 4 isolated discrete inputs and 4 isolated discrete outputs. Input channels accept 90-280VAC/VDC signals and output channels switch 24-280VAC signals at up to 3A AC load. NOTE: DIOH output channels switch AC loads only.
Discrete output channels have user configurable default output states which are set up on power up or module reset. In addition to performing standard discrete I/O, the channels can be configured to perform seven special functions: Pulse/Frequency Counter, Pulse/Frequency Counter with Debounce, Waveform Measurement, Time Between Events, Frequency Generator, Pulse Width Modulation (PWM), and One-Shot Generator. Up to four special functions can run simultaneously. High, Low, High-High and Low-Low alarms provide essential monitoring and warning functions to ensure optimum process flow and fail-safe applications. Field I/O connections are made through a pluggable terminal block.
Input-to-bus isolation is a robust 1500Vrms and channel-to-channel isolation is 300Vrms. Each individual channel has continuous overload and reverse connection protection in case of inadvertent wiring errors.
Frequently Asked Questions
Where do I download MAQ20 configuration software?
MAQ20 configuration is best performed with ReDAQ Shape software. We do have other software for download as well. Please check out the Software Download Center.
Note:The "MAQ20-945 Configuration Software Tool" was replaced with ReDAQ Shape software tool in 2017.
Can Dataforth provide calibration reports for modules I purchased?
Yes we can provide calibration reports for the modules that you purchased.
You can either
a) visit https://www.dataforth.com/TestDataReport.aspx to search for Test Report Datasheets by Serial Number or
b) you can send us a list of model numbers and their serial numbers to firstname.lastname@example.org
How do I save my module configuration in the Configuration Software Tool (MAQ20-945)?
The Configuration Software Tool for MAQ20 does not have project files that can be saved. Any adjustments you make to the configuration of your modules through the Configuration Software Tool will be saved to the modules themselves, and not to a file on your PC. It is only a tool to change the settings in the modules themselves.
How do I convert an RMS voltage to its corresponding peak voltage?
To convert an RMS voltage to its corresponding peak voltage, you simply take the RMS voltage value and multiply it by the square root of 2, or roughly 1.414.
For example, 1500Vrms corresponds to a peak voltage of 1500 * 1.414 = 2121 Vp
How are unlock keys used to license IPEmotion?
Unlock keys are generated from the serial number of the COM module of the system that you purchased. These unlock codes are also generated based on how many I/O modules are in the MAQ20 system. You won't be able to run the data acquisition process in IPEmotion unless you have entered the correct unlock code for your system and the I/O module count of your system is equal to or below the allotted I/O module count determined when the unlock code was generated.
For example, if you purchased an unlock key for a MAQ20-COM2 with 1 MAQ20-VO, 1 MAQ20-VDN, and 2 MAQ20-BRDG modules, this would correspond to an I/O module count of 4. If you attempted to run the acquisition process with this configuration, it would work perfectly. If you decided to remove the two MAQ20-BRDG modules, you would still be able to run the acquisition process. However, if you were to add a MAQ20-FREQ module to your system, bringing your total I/O module count to 5, IPEmotion will not let you start the data acquisition process until the I/O module count is back to 4 or lower.
If you have more than one MAQ20-COM module in your system, it is not necessary to enter additional unlock codes for the extra COM modules.
Where do I download the USB drivers for the MAQ20 to be used with ReDAQ Shape?
There are two places that you can download the USB drivers for MAQ20. If you haven't already downloaded ReDAQ Shape, you will be given the option to download the required USB drivers during the installation process. If you already have ReDAQ Shape downloaded and you somehow lost the USB drivers, you can download them from our website. The USB drivers for the 8B isoLynx SLX300 system are identical with the USB drivers for the MAQ20. Visit this link, scroll down to the "Drivers" section on the page and download "USB (Virtual Comm Port Driver)": https://www.dataforth.com/8Bisolynx_download.aspx
Is it possible to provide external power supply directly to the backplane rail instead through the MAQ20-COM2 front panel?
The MAQ20-COMx module has to be powered through its power connector and it powers the backbone to power the I/O modules.
If you powered the backbone too, then that power supply would fight the power supply from the COM module and they would likely damage each other.
How does the load resistance of a module affect the noise at the output?
Noise at the output of a module is independent of load resistance.
Can I export data from ReDAQ shape to a text file or Excel spreadsheet?
Yes, ReDAQ Shape offers the option to export data to a .txt file or Excel spreadsheet live without interrupting the data acquisition process. Simply click the "Open Data File" or "Open Excel File" button in the "Analyze" panel.
How are unlock codes used with ReDAQ Shape?
Unlock codes are generated based on the serial number of the COM module of the system you purchased. If you are running an unlicensed version of ReDAQ Shape you sill have access to all the features of the software, but are limited to 1 hour of usage until the software stops. Entering the unlock code associated with your MAQ20 system will remove the time limit and allow unlimited usage of ReDAQ Shape. You must purchase an unlock code for every COM module you are using in order to have unlimited usage of ReDAQ Shape.
Note: Licenses purchased for the Developer version of ReDAQ Shape are not compatible with the User version, and vice versa.
Can I copy and paste data from ReDAQ Shape while in acquisition?
Yes, ReDAQ Shape has the ability to directly copy and paste raw data from the "Analyze" tab, without interrupting the acquisition process. However, you must use the "Copy To Clipboard" button located at the top left corner of the raw data table - using keyboard commands or right clicking and selecting "Copy" will not work.
Is it possible to send a remote setpoint via Modbus/TCP to a PID loop running your ReDAQ Shape software on MAQ20 hardware?
Yes, it is possible to send a remote setpoint via Modbus/TCP to PID loop running in ReDAQ Shape by writing to the Modbus registers of the MAQ20 hardware. Please see the address map at the end of the MAQ20 PID Controller User Manual
Does the MAQ20 Python API support USB connection?
Currently, the MAQ20 Python API only supports Ethernet connection.
Does USB have a faster response time than Ethernet when communicating with the MAQ20?
The MAQ20 ideally has equally fast response times regardless of whether you use USB or Ethernet connection. Other variables outside of the MAQ20 can influence this response time however, such as if you are using a USB to Ethernet adapter or if the MAQ20 is part of a larger company network.
Can the MAQ20 save data directly to a SQL database?
No, the MAQ20 cannot save or export data directly to a SQL database. ReDAQ Shape can export data directly to a .txt, .csv or Excel file, and then the data could be extracted from those files to be uploaded to a SQL database.
Is there a demo version available for ReDAQ Shape?
Yes, the version available for download from our website can serve as a demo if you do not have an unlock code. The unlicensed software will run for 30 minutes with full functionality with no license. Once the 30 minutes is up, you can restart the program to reset the 30 minute time for as many times as you would like.
What file/formats are supported/produced with ReDAQ Shape?
Data logged in the Analyze panel in ReDAQ Shape can be exported to a .txt file or Excel file. The SD Card Logger can generate .csv files as well.
Will I run into any problems operating my MAQ20 system for 60 days straight?
No, we have many customers that use our MAQ20 system 24/7, 365 days a year. We also have a weather station onsite that uses a MAQ20 system continuously running 365 days of the year. Please visit https://www.dataforth.com/maq20-remote-access-viewer.aspx to access the weather station demo.
Can I save the settings of my MAQ20 module to EEPROM outside of ReDAQ Shape?
Yes, refer to the address map of the module you are using which can be found at the end of that module's hardware user manual. There will be a register "Save to EEPROM." Writing the appropriate value as described in the address map to this register will save your module's current settings to EEPROM.
Can I disconnect my MAQ20 from my PC and have the system to continue to log data?
If you start a standard logging process (i.e. clicking "run" in ReDAQ Shape or "store" in IPEmotion), disconnecting your MAQ20 system from the PC will terminate the log.
However, if you use the MAQ20s SD Card Logger, you can start a data log and disconnect the MAQ20 and it will continue to log data until it reaches the end of the log based on the parameters you have specified (number of samples, time interval, etc.)
Can I still export my acquired data to a text file or Excel spreadsheet with the User version of ReDAQ Shape?
Yes, these options are available in both the User and Developer versions of ReDAQ Shape.
I tried to print a test data sheet for my MAQ20 module on your website but I couldn’t. Is there anything special I need to do to get a test data sheet for my MAQ20 module?
MAQ20 test data sheets are not available on our website. However, test data sheets for purchased MAQ20 modules are available upon request. Please contact our Customer Service Team at email@example.com