Each DSCA30/31 voltage input module provides a single channel of analog input which is filtered, isolated, amplified, and converted to a high-level voltage output. Signal filtering is accomplished with a five-pole filter which provides 85dB of normal-mode rejection at 60Hz and 80dB at 50Hz. An anti-aliasing npole is located on the field side of the isolation barrier, and the other four poles are on the system side. After the initial field-side filtering, the input signal is chopped by a proprietary chopper circuit. Isolation is provided by transformer coupling, again using a proprietary technique to suppress transmission of common mode spikes or surges.
Module output is either voltage or current. For current output models a dedicated loop supply is provided at terminal 3 (+OUT) with loop return located at terminal 4 (-OUT). The system-side load may be either floating or grounded.
Special input circuits provide protection against accidental connection of power-line voltages up to 240VAC and against transient events as defined by ANSI/IEEE C37.90.1. Protection circuits are also present on the signal output and power input terminals to guard against transient events and power reversal. Signal and power lines are secured to the module using screw terminals which are in pluggable terminal blocks for ease of system assembly and reconfiguration.
The modules have excellent stability over time and do not require recalibration, however, zero and span settings are adjustable up to ±5% to accommodate situations where fine-tuning is desired. The adjustments are made using potentiometers located under the front panel label and are non-interactive for ease of use.
Frequently Asked Questions
Can Dataforth provide calibration reports for modules I purchased?
Yes we can provide calibration reports for the modules that you purchased.
You can either
a) visit https://www.dataforth.com/TestDataReport.aspx to search for Test Report Datasheets by Serial Number or
b) you can send us a list of model numbers and their serial numbers to firstname.lastname@example.org
Does Dataforth have any DSCA modules that can operate on a 12Vdc power supply?
Dataforth does not have any custom modules that run on 12VDC power. Most DSCA modules require a minimum power supply voltage of 15VDC while some require a minimum of 19VDC. Both are suitable for use with nominal 24VDC power supplies over the full operating temperature range of -40C to +85C. Dataforth offers a line of accessory power supplies, PWR-PS5RxW, which have been qualified for use with the DSCA product line. https://www.dataforth.com/catalog/pdf/PWR-PS5RxW.pdf
How do I convert an RMS voltage to its corresponding peak voltage?
To convert an RMS voltage to its corresponding peak voltage, you simply take the RMS voltage value and multiply it by the square root of 2, or roughly 1.414.
For example, 1500Vrms corresponds to a peak voltage of 1500 * 1.414 = 2121 Vp
What is the output resolution of the DSCA series?
The DSCA series is completely analog, so the output resolution cannot be expressed in terms of bits as it is not a digital signal. The only thing that would cause any uncertainty/lack of clarity in your output signal would be the output ripple and noise, which is rated at a typical value of 0.025% span RMS as listed in the datasheet.
Is the calibration of Dataforth modules traceable to NIST standards?
Yes, calibration of Dataforth modules is traceable to NIST standards.
Where can I find the MTBF of my module?
Information on MTBF for SCM5B, SCM7B, 8B and DSCA is available on our website. Please see application note AN802 for more details. Application notes can be found under the "Literature" tab on the top navigation bar.
If the input range of my signal conditioner is -1V to +1V and the output range is 0 to 10V, does this mean that it ignores polarity?
A signal conditioner with these I/O ranges does not mean that the module ignores the polarity of your voltage input. The output of voltage input modules are scaled linearly, meaning an input of -1V would correspond to an output of 0V, an input of 0V would correspond to an output of 5V, an input of +1V would correspond to an output of 10V, and so on.
How does the load resistance of a module affect the noise at the output?
Noise at the output of a module is independent of load resistance.
Can the DSCA30/31-xx be modified to have a faster response time?
The DSCA30/31-xx series cannot be modified to have a faster response time. However, the DSCA40/41-xx series is the direct equivalent of the DSCA30/31-xx series, but with a wider bandwidth and faster response time.
Can I measure a small potential on top of a 1500V signal with the DSCA30/31 module?
The DSCA30/31 has an input to output isolation of 1500Vrms, meaning that it is possible to measure small potentials on top of a 1500V common mode voltage. This will not damage the module.
Will I damage the input of my DSCA40-02 if I apply a 12V signal?
All DSCA40 and DSCA30 modules are input protected up to a continuous 240Vrms signal. 12V is well below that rating and will not damage the module.
How far can I overrange my DSCA30/31/40/41 module? What will the effects be on the module/output?
The overrange capability is approximately 10% of the input range unless otherwise specified in the datasheet. Beyond that level the output will become nonlinear and will clamp either at a reference or power supply rail. Accuracy and linearity are not guaranteed over the minimum and maximum output.
The module will not be damaged in any way unless the input exceeds the input protection specification, which is 240Vrms continuous.
What size wires do the DSCA modules accept?
DSCA module screw terminals are rated to wire gage AWG: 28 – 12.
Was this content helpful?
View Dataforth cross-reference data.
- No cross reference is available.
The information available through this competitive cross reference guide are based upon product catalog information obtained from a variety of sources. The competitive cross reference information is being provided to you free of charge for your use. While Dataforth Corp has used reasonable efforts to ensure data accuracy, Dataforth Corp does not guarantee that it is error-free, nor does Dataforth Corp make any other representation, warranty or guarantee that the information is accurate, correct, reliable or up-to-date. Dataforth Corp expressly disclaims all implied warranties regarding this information, including but not limited to any implied warranties of merchantability or fitness for a particular purpose.
This information is provided only as a convenience on an "as is" basis and Dataforth Corp. or its representatives or distributors are not responsible for any incorrect, inaccurate, or incomplete information. You are solely responsible for (1) selecting the appropriate Dataforth products for your application, (2) designing, validating and testing your application, and (3) ensuring your application meets applicable standards, and any other safety, security, or other requirements.